We can provide annual maintenance contract for complete fire fighting system including hydrant system,sprinkler system fire alarm systems and fire extinguishers in comprehensive or non comprehensive ways as per client requirement
AMC Of Fire Extinguishers:
They do this through regular check and updates on each device. From cleaning dirt on the exteriors to checking internal mechanisms, the services team leaves no detail unchecked.
Corrosionon the extinguisher's body can lead to leakage. Hence, the extinguisher is checked for dust deposits and dents.
Then, the safety seal is checked to ensure that it is intact and has not been tampered with. Instructions sticker is checked too at this stage.
The discharge nozzle is checked to ensure that it is unclogged. After cleaning and removing the dust from the nozzle and hose small amount of sealant to the thread end applied and valve assembled tightly to ensure no leakage.
The functioning and circuitry of the Instalert bracket alarm are checked to ensure that the fire alarm goes off when the extinguisher is lifted from its bracket.
Lowered pressure can result in a redundant fire extinguisher. The Service engineers use a special magnetic device to check that the pressure gauge is in perfect working condition.
According to the law, and to ensure safety, a CO2 extinguisher must be weighed once every three months to check for leakage. Ceasefire’s engineers weigh the extinguisher at your premises on a highly sensitive and very accurate electronic scale that detects the slightest of fluctuations in the extinguisher’s weight.
The extinguisher is then scanned for signs of wear and tear or breakage of components like the wheels, the base etc. The materials such as base bottom, rubber parts, hose etc which are found to have deteriorated over time due to aging or due to over exposure to temperatures and moisture are replaced.
Finally the fire extinguisher is polished with the wax polish; brass and gunmetal with metal polish, and plastic component with wet cloth dipped in mild soap water.